IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Published (Last):||10 February 2017|
|PDF File Size:||19.44 Mb|
|ePub File Size:||16.34 Mb|
|Price:||Free* [*Free Regsitration Required]|
IEEE IEEE Standard for Series Capacitors in Power Systems Capacitors and assemblies of capacitors, insulation 6009-95, switching, protective equipment, and control accessories that form a complete bank 600999-5 inserting in series with a transmission line are applied. Systematic directions toward proper solutions of various applications are provided.
Its object is to give information in terms of methods, modeling and examples, allowing for the application of the approaches presented in IECand for the selection of insulation levels of equipment or installations, as defined in IEC More complex and special solutions requiring study by experienced engineers is described, but specific solutions are not always given.
This standard also specifies requirements and tests for metal-oxide surge arresters with internal series gaps, with rated voltages of 52KV and below Preview Surge arresters ief Part 7: Fuses and other overcurrent protection devices Substations, surge arresters.
IEC | IEC Webstore
An additional section discusses several special methods that may be used to improve lightning performance. The requirements for human safety are not covered by this standard. This standard recommends that the selected withstand voltages should be associated with the highest voltage for equipment. Surge arrester residual voltage is a major parameter 600099-5 which most users have paid a lot of attention to when selecting the type and rating.
It also gives the lists of the standard withstand voltages from which the rated withstand voltages should be selected. In Annex J, some aspects regarding the old type of SiC gapped arresters are discussed. Click to learn more. Selection and application recommendations. See Complete Overview C Your basket is empty.
Metal-oxide surge arresters with external series gap EGLA for overhead transmission and distribution lines of a. It applies to gapless metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in IEC Contact us svenska Login.
Insulation Coordination Standards Insulation co-ordination – Part 1: Learn more about the cookies we use ifc how to change your settings. What makes this amendment so unique is that oec is virtually identical to the test procedure published in IEC in You may find similar items within these categories by selecting from the choices below:. The protective equipment oec mentioned in clauses 1.
BS EN 60099-5:2013
You may experience issues viewing this site in Internet Explorer ie, 10 or This standard applies to devices for separate mounting and to devices supplied integrally with other equipment. Subscribe on standards with our subscription service.
Protective equipment for series capacitor banks This part of IEC covers protective equipment for series capacitor banks, 60909-5 a size larger than 10 Mvar per phase. Do you need a multi-user copy? Grounding electrode techniques, pole ground values, and system ground grid values are not addressed or considered in this document.
These are surge arresters consisting of one or more non-linear resistors which may be in series with single or multiple spark gaps.
Metal-oxide surge arresters without gaps for a. Report error on page.
They are not used in general to provide surge protection. TC 37 – Surge arresters rss.
BS EN – Surge arresters. Selection and application recommendations
Surge arresters containing both series and parallel gapped structures – Rated 52 kV and less This standard applies to all metal-oxide surge arresters with gaps and housed in either porcelain or polymeric housings.
This new ief covers new mechanical test requirements for polymer and porcelain housed arresters. These ie apply specifically to electric utility systems and do not recognize the neutral grounding requirements for dispersed storage and generation.
We accept all major credit cards American Express, Mastercard and VisaPayPal and bank transfers as form of payment. Take the smart route to manage medical device compliance. Related publications IEC September Replaced By: Search all products by.