CJ1W-PRM21 Omron Automation and Safety Controllers CJ1 Profibus Master datasheet, inventory, & pricing. This article (NJ base) explains how to setup the configuration for the NJ with a CJ1W-PRM21 Profibus communication unit connecting. Buy Omron CJ1W Series PLC I/O Module, 31 x 90 x 68 mm CJ1W-PRM Browse our latest plc-i-o-modules offers. Free Next Day Delivery.
|Published (Last):||18 November 2008|
|PDF File Size:||11.36 Mb|
|ePub File Size:||13.46 Mb|
|Price:||Free* [*Free Regsitration Required]|
I fj1w programed the functions send and recv acording with the master configuration. I’m almost sure that this bosch unit provides profibus connection. Hello Daniel, Thanks for your answer.
Hello, the BF led blink in the omron master, the slave appear only with pgm21 led run. I was sure that I’ve tried all but I didn’t. Share this post Link to post Share on other sites.
Seeing the scan returns error with DTM version 1. Sign in Already have an account? Have a look at the following FAQ and attached links: Here I have que diagnostic of the cp slave.
CX-Configurator CJ1W-PRM21 connection problems.
If this is already done, it would be good to see how they have been configured. But it’s possible that the problem is the hardware config. I made a diagnostic to de cp and appear this error: Hope this helps, Daniel Chartier.
Site Explorer Orm21 Explorer. It supposed to be toolbus usb in configuration tab, and now i can use test, and go online options without any errors. The master tell me that the slave have a invalid response. When i try to use scan option i get another error:. When i try to use scan option i get another error: I’ve made mistake, because communication module is diffirent than I mentioned before. Sign up for a new account in our community. Hello Ariel; In your diagnostic messages a few stand out, at first glance ArielP 10!!
Try to run the AutoUpdate so you’ll get a newer version if you have a registered copy. Edited 21 March by malyalewariat.
I have no idea. Follow us on Twitter Youtube.
This contribution was helpful to 1 thankful Users dchartier. Sign In Sign Up. You need to be a member in order to leave a comment.
I should do any thing else, Thaks. So many communication protocols to choose.
Create an account or sign in to comment You need to be a member in order to leave a comment Create an account Sign up for a new account in our community. The module was update to firmware V3, but I have only in step 7 the product versions 1 and 2. What about those errors? It is profibus slave.
All about Decentral Peripherie. I can now pgm21 diagnostic option and I can see states of plc and module. Started by malyalewariat18 March prm21 cj1w bus profibus.
myOMRON Europe: Services & Support
Product Support Services Forum mySupport. Am I missing CX-Server? When I use “Test” option or just go online I get errors: I configured in S7 project the slave parameters. The GSD file you will find here: Posted 21 March edited.